Henan Hengan Boiler Co., Ltd. will talk about the contents of boiler auxiliary machine inspection in operation. Details are welcome to inquire: 1314001120
1. Fan: The manhole door is tightly closed, the bearing temperature indication is correct, the temperature is <70 ° C, the front and rear bearing oil levels are normal 1 / 2-2 / 3, the bearing oil level is normal, the return water is normal, the return water temperature is <40 ° C, the shaft Vibration <0.1MM, string axis <2 --- 4MM, fan rotates normally, no friction, abnormal noise, no odor.
2. There is no loosening of the foundation screw of the motor, the shield of the wheel screws is intact, the grounding wire is firm, the oil level of the front and rear bearings is normal, the oil level gauge is clear, the oil quality is good, the bearing temperature is <70 ℃, the motor temperature is <100 ℃ <0.1MM, serial axis <2 --- 4MM, the motor rotates normally, no friction check, abnormal noise.
3. Baffle: The inlet adjustment baffle moves flexibly, the actuator is well connected to the connecting rod, and the scale indication is correct. The local switch is in the-remote control-position. The outlet baffle moves flexibly. The actuator is well connected to the connecting rod, and the scale indication is correct. , Local switch, in-remote control-position 1/2-2/3.
4. The oil level of the oil tank in the petrol station is normal, the oil quality is good, the hydraulic pressure is adjusted to 2.5-3.5MPA, the hydraulic oil leaks, and the oil returns to normal. The normal oil quantity is sufficient, the system has no oil leakage, the cooling water is unblocked, the incoming water is normal, and the return water temperature is <40 ° C.
5. The bearing box oil level is normal, the oil quality is good, and the temperature is <60 ℃.
6. Others: The accident button is intact and the protective cover is complete.